Red Lion Crimson 3.1
1. EXECUTIVE SUMMARY
- CVSS v3 7.5
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Red Lion
- Equipment: Crimson 3.1
- Vulnerabilities: NULL Pointer Dereference, Missing Authentication for Critical Function, Improper Resource Shutdown or Release
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to create a denial-of-service condition, read and modify the database, and leak memory data.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Crimson 3.1 for the DA10D Protocol Converter are affected:
- Crimson 3.1: Build versions prior to 3119.001
3.2 VULNERABILITY OVERVIEW
A NULL pointer deference vulnerability has been identified in the protocol converter. An attacker could send a specially crafted packet that could reboot the device.
The default configuration of the affected product allows a user to be able to read and modify the database without authentication.
An attacker could send a specially crafted message that could leak arbitrary memory locations.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: United States
Marco Balduzzi, Ryan Flores, Philippe Lin, Charles Perine, Ryan Flores, Rainer Vosseler working with Trend Micro Zero Day Initiative reported these vulnerabilities to CISA.
Red Lion recommends users update to build 3119.001 or later.
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.