Fieldcomm Group HART-IP and hipserver
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Fieldcomm Group
- Equipment: HARP-IP Developer kit, hipserver
- Vulnerability: Stack-based Buffer Overflow
2. RISK EVALUATION
Successful exploitation of this vulnerability could crash the device being accessed; a buffer overflow condition may allow remote code execution.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following products and versions are affected:
- HART-IP Developer kit, Release 126.96.36.199
- hipserver, Release 3.6.1
3.2 VULNERABILITY OVERVIEW
A malicious attacker could exploit this interface by constructing HART-IP messages with sufficiently large payloads to overflow the internal buffer and crash the device, or obtain control of the device.
- CRITICAL INFRASTRUCTURE SECTORS: Commercial Facilities, Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: United States
Reid Wightman from Dragos, Inc., reported this vulnerability to Fieldcomm.
Fieldcomm Group recommends users restrict access to the computers or devices running the software. Users of hipserver should immediately upgrade source code to v3.7.0 or later. For technical support, please visit https://support.fieldcommgroup/ and file a support ticket. For more information, please see the Fieldcomm Group security page.
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.