All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 7.5
- ATTENTION: Exploitable remotely/low attack complexity
- Vendor: CODESYS GmbH
- Equipment: CODESYS Gateway Server
- Vulnerability: Heap Based Buffer Overflow
2. UPDATE INFORMATION
This updated advisory is a follow-up to the original advisory titled ICSA-15-258-02 3S CODESYS Gateway Server Buffer overflow Vulnerability that was published September 15, 2015, on the ICS webpage at cisa.gov/ics.
3. RISK EVALUATION
Successful exploitation of this vulnerability could cause a buffer overflow condition that may allow remote code execution.
4. TECHNICAL DETAILS
4.1 AFFECTED PRODUCTS
The following versions of CODESYS Gateway Server, a connection management server, are affected:
--------- Begin Update A Part 1 of 2 ---------
- CODESYS Gateway Server: Version 126.96.36.199 and prior
--------- End Update A Part 1 of 2 ---------
4.2 VULNERABILITY OVERVIEW
The affected product is vulnerable to multiple heap-based buffer overflow vulnerabilities that may allow remote code execution.
- CRITICAL INFRASTRUCTURE SECTORS: Multiple
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
Josep Pi Rodriguez, working with Trend Micro’s Zero Day Initiative, reported this vulnerability to CISA.
--------- Begin Update A Part 2 of 2 ---------
CODESYS has released Version 188.8.131.52 of the CODESYS Gateway Server to address this vulnerability. This CODESYS Gateway Server version is also part of the CODESYS Development System setup Version 184.108.40.206 and is available for download (login required).
--------- End Update A Part 2 of 2 ---------
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls and isolate them from business networks.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize VPN is only as secure as its connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage at cisa.gov/ics. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage at cisa.gov/ics in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.