All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
CVSS v3 8.2
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Siemens
- Equipment: S7-400 CPUs
- Vulnerabilities: Improper Input Validation
2. UPDATE INFORMATION
This updated advisory is a follow-up to the original advisory titled ICSA-18-317-02 Siemens S7-400 CPUs (Update A) that was published November 13, 2018, on the NCCIC/ICS-CERT website.
3. RISK EVALUATION
Successful exploitation of these vulnerabilities could crash the device being accessed which may require a manual reboot or firmware re-image to bring the system back to normal operation.
4. TECHNICAL DETAILS
4.1 AFFECTED PRODUCTS
Siemens reports that the vulnerabilities affect the following SIMATIC S7-400 products:
--------- Begin Update B Part 1 of 1 ---------
- S7-400 DP V7 CPU family (including SIPLUS variants): All versions
- S7-400 H V4.5 and below CPU family (including SIPLUS variants): All versions
- S7-400 H V6 CPU family (including SIPLUS variants): All versions prior to V6.0.9
- S7-400 PN/DP V6 and below CPU family (including SIPLUS variants): All versions
- S7-410 CPU family (including SIPLUS variants): All versions prior to V8.2.1
--------- End Update B Part 1 of 1 ---------
4.2 VULNERABILITY OVERVIEW
Specially crafted packets sent to Port 102/TCP via Ethernet interface, via PROFIBUS, or via multi-point interfaces (MPI) could cause the affected devices to go into defect mode. Manual reboot is required to resume normal operation.
Specially crafted packets sent to Port 102/TCP via Ethernet interface via PROFIBUS or MPI could cause a denial-of-service condition on affected devices. Recovery may require flashing with a firmware image.
If access protection is not configured, no privileges are required to exploit this vulnerability.
- CRITICAL INFRASTRUCTURE SECTORS: Chemical, Critical Manufacturing, Energy, Food and Agriculture, Healthcare and Public Health, Transportation.
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
Zhang JiaWei and Qing YuLong from CNCERT/CC reported these vulnerabilities to Siemens.
Siemens recommends implementing the following mitigations:
- Configure protection Level 3 (read/write protection) to mitigate CVE-2018-16557
- Restrict network access to affected devices; restrict network access to Port 102/TCP for Ethernet interfaces.
- For SIMATIC S7-CPU 410 CPUs: Activate field interface security in PCS 7 v9.0, use a SIMATIC CP443-1 Adv. to communicate with ES/OS, and update to Version 8.2.1:
- For SIMATIC S7-400H V6: Update to Version 6.0.9
- Apply defense-in-depth:
As a general security measure, Siemens strongly recommends protecting network access to devices with appropriate mechanisms. In order to operate the devices in a protected IT environment, Siemens recommends configuring the environment according to Siemens’ operational guidelines for industrial security (download: https://www.siemens.com/cert/operational-guidelines-industrial-security), and following the recommendations in the product manuals.
For more information on these vulnerabilities and associated software updates, please see Siemens security advisory SSA-113131 on their website:
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.