All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 6.3
- ATTENTION: Exploitable remotely/low attack complexity
- Vendor: Trane
- Equipment: Building Automation Controllers (Tracer SC)
- Vulnerability: Cross-site Scripting
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an attacker to redirect a user to a malicious webpage and steal the user’s cookie.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Trane building automation products, a device used to coordinate building controls, is affected:
- Tracer SC: Firmware v3.8 and prior
3.2 VULNERABILITY OVERVIEW
The affected product’s web application does not properly neutralize the input during webpage generation, which could allow an attacker to inject code in the input forms.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Ireland
Chizuru Toyama of TXOne IoT/ICS Security Research Labs of Trend Micro reported this vulnerability to CISA.
Trane has identified the following specific mitigations for the affected products:
- Users upgrade Tracer SC controllers running firmware v3.8 and prior, to firmware v4.4 SP7 or higher. Users should contact a regional Trane office to install updated firmware or request additional information and reference Trane service database number HUB-207592.
- Tracer SC is no longer actively developed, tested, or sold. Tracer SC will be considered end-of-life on December 31, 2022. Trane recommends users identify a migration plan to replace the Tracer SC controller with the Tracer SC+ controller, which can function as a drop-in replacement for Tracer SC, providing significant security upgrades.
In addition to the specific recommendations above, Trane recommends the following best practices as an additional protection against this and other controller vulnerabilities:
- Restrict physical controller access to trained and trusted personnel.
- Isolate Tracer controls from other network devices using virtual local area networks (VLAN), and from the Internet using a firewall with no exposed inbound ports.
- Use secure remote access solutions such as Trane Connect Remote Access.
- Ensure user credentials are not shared and follow best practices for appropriate complexity (e.g., strong passwords).
- Have a well-documented process and owner to ensure regular software/firmware updates and to keep systems up to date.
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.