All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 7.5
- ATTENTION: Exploitable remotely/low attack complexity
- Vendor: Mitsubishi Electric
- Equipment: MELSEC and MELIPC Series
- Vulnerabilities: Uncontrolled Resource Consumption, Improper Handling of Length Parameter Inconsistency, Improper Input Validation
2. UPDATE INFORMATION
This updated advisory is a follow up to the advisory update titled ICSA-21-334-02 Mitsubishi Electric MELSEC and MELIPC Series (Update C) that was published June 7, 2022, to the ICS webpage on cisa.gov/ics.
3. RISK EVALUATION
Successful exploitation of these vulnerabilities may allow a remote attacker to cause a denial-of-service condition. A system reset is required for recovery.
4. TECHNICAL DETAILS
4.1 AFFECTED PRODUCTS
The following versions of MELSEC series CPU modules and MELIPC Series Industrial Computers are affected:
- MELSEC iQ-R Series R00/01/02CPU: Firmware Versions 24 and prior
- MELSEC iQ-R Series R04/08/16/32/120(EN)CPU: Firmware Versions 57 and prior
- MELSEC iQ-R Series R08/16/32/120SFCPU: All versions
- MELSEC iQ-R Series R08/16/32/120PCPU: Firmware Versions 29 and prior
- MELSEC iQ-R Series R08/16/32/120PSFCPU: Firmware Versions 08 and prior
- MELSEC iQ-R Series R16/32/64MTCPU: Operating system software Versions 23 and prior
---------- Begin Update D Part 1 of 4 ----------
- MELSEC iQ-R Series R12CCPU-V: Firmware Versions 16 and prior
---------- End Update D Part 1 of 4 ----------
- MELSEC Q Series Q03UDECPU, Q04/06/10/13/20/26/50/100UDEHCPU: The first 5 digits of serial No. 23121 and prior
- MELSEC Q Series Q03/04/06/13/26UDVCPU: The first 5 digits of serial No. 23071 and prior
- MELSEC Q Series Q04/06/13/26UDPVCPU: The first 5 digits of serial No. 23071 and prior
- MELSEC Q Series Q12DCCPU-V, Q24DHCCPU-V(G), Q24/26DHCCPU-LS: The first 5 digits of serial No. 24031 and prior
- MELSEC Q Series MR-MQ100: Operating system software version F and prior
- MELSEC Q Series Q172/173DCPU-S1: Operating system software version W and prior
- MELSEC Q Series Q172/173DSCPU: All versions
- MELSEC Q Series Q170MCPU: Operating system software version W and prior
- MELSEC Q Series Q170MSCPU(-S1): All versions
- MELSEC L Series L02/06/26CPU(-P), L26CPU-(P)BT: The first 5 digits of serial No. 23121 and prior
---------- Begin Update D Part 2 of 4 ----------
- MELIPC Series MI5122-VW: Firmware Versions 05 and prior
---------- End Update D Part 2 of 4 ----------
4.2 VULNERABILITY OVERVIEW
The product does not properly control the allocation and maintenance of a limited resource, thereby enabling an actor to influence the amount of resources consumed, eventually leading to the exhaustion of available resources.
The product parses a formatted message or structure, but it does not handle or incorrectly handles a length field that is inconsistent with the actual length of the associated data.
The product receives input or data, but it does not validate or incorrectly validates that the input has the properties required to process the data safely and correctly.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Japan
Mitsubishi Electric reported these vulnerabilities to CISA.
Mitsubishi Electric has corrected the vulnerabilities in the following products and intends to do the same with other products in the near future.
MELSEC iQ-R Series
- R00/01/02CPU: Firmware Versions 25 or later
- R04/08/16/32/120(EN)CPU: Firmware Versions 58 or later
- R08/16/32/120PCPU: Firmware Versions 30 or later
- R08/16/32/120PSFCPU: Firmware Versions 09 or later
- R16/32/64MTCPU: Operating system software Version 24 or later
---------- Begin Update D Part 3 of 4 ----------
- R12CCPU-V: Firmware Versions 17 or later
---------- End Update D Part 3 of 4 ----------
MELSEC Q Series
- Q03UDECPU, Q04/06/10/13/20/26/50/100UDEHCPU: The first 5 digits of serial No. 23122 or later
- Q03/04/06/13/26UDVCPU: The first 5 digits of serial No. 23072 or later
- Q04/06/13/26UDPVCPU: The first 5 digits of serial No. 23072 or later
- Q12DCCPU-V, Q24DHCCPU-V(G), Q24/26DHCCPU-LS: The first 5 digits of serial No. 24032 or later
- MR-MQ100: Operating system software version G or later
- Q172/173DCPU-S1: Operating system software version X or later
- Q170MCPU: Operating system software version X or later
MELSEC L Series
- L02/06/26CPU(-P), L26CPU-(P)BT: The first 5 digits of serial No. 23122 or later
---------- Begin Update D Part 4 of 4 ----------
- MI5122-VW: Firmware Versions 06 or later
---------- End Update D Part 4 of 4 ----------
Mitsubishi Electric also recommends users take the following mitigation measures to minimize the risk of exploiting these vulnerabilities:
- Use a firewall or virtual private network (VPN), etc. to prevent unauthorized access when Internet access is required.
- Use a LAN and block access from untrusted networks and hosts through firewalls.
- Use the remote password function or IP filter function to block access from untrusted hosts. For details on the remote password function and IP filter function, please refer to the following manual for each product.
- MELSEC iQ-R Ethernet User’s Manual (Application) 1.13 Security "Remote password" "IP filter"
- MELSEC iQ-R Motion Controller Programming Manual (Common) 6.2 Security Function "IP filter"
- MELSEC iQ-R C Controller Module User's Manual (Application) 6.6 Security Function "IP filter"
- QnUCPU User’s Manual (Communication via Built-in Ethernet Port) CHAPTER 10 REMOTE PASSWORD
- MELSEC-L CPU Module User's Manual (Built-In Ethernet Function) CHAPTER 11 REMOTE PASSWORD
- MELIPC MI5000 Series User's Manual (Application) 11.3 IP Filter Function
For specific update instructions and additional details see the Mitsubishi Electric advisory.
CISA recommends users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize VPN is only as secure as its connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on cisa.gov/ics Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on cisa.gov/ics in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.