All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 7.5
- ATTENTION: Exploitable remotely/low attack complexity
- Vendor: Mitsubishi Electric
- Equipment: MELSEC-F Series
- Vulnerability: Improper Initialization
2. RISK EVALUATION
Successful exploitation of this vulnerability may cause a denial-of-service condition in the affected product.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of MELSEC-F Series with FX3U-ENET, an Ethernet-Internet block, are affected:
- FX3U-ENET: Firmware Version 1.16 and prior
- FX3U-ENET-L: Firmware Version 1.16 and prior
- FX3U-ENET-P502: Firmware Version 1.16 and prior
3.2 VULNERABILITY OVERVIEW
An attacker could send a specially crafted packet that could create a denial-of-service condition in the communication function of the product. A system reset is required for recovery.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Japan
Mitsubishi Electric reported this vulnerability to CISA.
Mitsubishi Electric corrected this vulnerability in the following products and versions, as follows:
- FX3U-ENET: Firmware Version 1.17 or later
- FX3U-ENET-L: Firmware Version 1.17 or later
- FX3U-ENET-P502: Firmware Version 1.17 or later
Mitsubishi Electric also recommends users take the following mitigation measures to minimize the risk of exploiting this vulnerability:
- Use a firewall, VPN, or other barrier to prevent unauthorized access when Internet access is required.
- Use within a LAN and block access from untrusted networks and hosts through firewalls.
For specific update instructions and additional details see the Mitsubishi Electric advisory.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.