All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 8.4
- ATTENTION: Exploitable remotely/low attack complexity
- Vendor: Johnson Controls Inc.
- Equipment: Metasys
- Vulnerability: Server-side Request Forgery
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an authenticated attacker to inject malicious code into the MUI PDF export feature.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Metasys, a building automation system, are affected:
- Metasys ADS/ADX/OAS Versions 10 and 11
3.2 VULNERABILITY OVERVIEW
An authenticated attacker could inject malicious code into the MUI PDF export feature, which could result in server-side request forgery.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Ireland
Tony West reported this vulnerability to Johnson Controls Inc.
Johnson Controls recommends upgrading to the current version of Metasys
- Update Metasys ADS/ADX/OAS Version 10 with patch 10.1.5
- Update Metasys ADS/ADX/OAS Version 11 with patch 11.0.2
For more detailed mitigation instructions, please see Johnson Controls Product Security Advisory JCI-PSA-2022-02 v1
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize VPN is only as secure as its connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
CISA also recommends users take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.