All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.0
- ATTENTION: Exploitable remotely
- Vendor: Mitsubishi Electric
- Equipment: MELSEC-Q Series C Controller Module
- Vulnerability: Heap-based Buffer Overflow
2. RISK EVALUATION
Successful exploitation of this vulnerability could cause a denial-of-service condition or allow remote code execution.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of MELSEC-Q Series C Controller Module using Wind River VxWorks Version 6.4 are affected:
- Module Q12DCCPU-V: First 5 digits of serial number 24031 and prior
3.2 VULNERABILITY OVERVIEW
The affected product uses a vulnerable version of Wind River VxWorks that could result in a heap-based buffer overflow in the DHCP client
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Japan
Mitsubishi Electric reported this vulnerability to CISA.
Mitsubishi Electric recommends the following:
- Update to 24032 (first 5 digits of serial number) or later. Contact a Mitsubishi Electric representative for more information.
- Disable the DHCP function in “Security Settings” of the C language controller settings/monitor tool if the product is in “Extended mode” and the DHCP client function is not required.
- Update DHCP server to the latest version.
- Use a firewall or virtual private network (VPN), etc. to prevent unauthorized access when Internet access is required.
- Use within a trusted LAN that is properly divided by routers and firewalls.
For more information see Mitsubishi Electric’s advisory 2022-001
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability. This vulnerability has a high attack complexity.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.