All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 7.5
- ATTENTION: Exploitable remotely/low attack complexity
- Vendor: Siemens
- Equipment: CPC80 Firmware of SICAM A8000
- Vulnerability: Missing Release of Resource after Effective Lifetime
2. RISK EVALUATION
Successful exploitation of this vulnerability could crash the device being accessed; a buffer overflow condition may allow remote code execution.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following Siemens products are affected:
- CP-8000 MASTER MODULE WITH I/O -25/+70°C (6MF2101-0AB10-0AA0): All versions prior to CPC80 v16.30
- CP-8000 MASTER MODULE WITH I/O -40/+70°C" (6MF2101-1AB10-0AA0): All version prior to CPC80 v16.30
- CP-8021 MASTER MODULE (6MF2802-1AA00): All versions prior to CPC80 v16.30
- CP-8022 MASTER MODULE WITH GPRS (6MF2802-2AA00): All versions prior to CPC80 v16.30
3.2 VULNERABILITY OVERVIEW
The affected product is vulnerable when using the HTTPS server under specific conditions, affected devices do not properly free resources. This could allow an unauthenticated remote attacker to put the device into a denial-of-service condition.
- CRITICAL INFRASTRUCTURE SECTORS: Energy
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
Michael Messner from Siemens Energy reported this vulnerability to Siemens.
Siemens recommends updating to the latest version:
- CP-8000 MASTER MODULE WITH I/O -25/+70°C (6MF2101-0AB10-0AA0): Update to versions CPC80 v16.30 or later
- CP-8000 MASTER MODULE WITH I/O -40/+70°C" (6MF2101-1AB10-0AA0): Update to versions CPC80 v16.30 or later
- CP-8021 MASTER MODULE (6MF2802-1AA00): Update to versions CPC80 v16.30 or later
- CP-8022 MASTER MODULE WITH GPRS (6MF2802-2AA00): Update to versions CPC80 v16.30 or later
Siemens has identified the following specific workarounds and mitigations that customers can apply to
reduce the risk:
- Limit access to port 443/tcp to trusted IP addresses and avoid opening untrusted files from unknown sources in affected products.
As a general security measure, Siemens recommends protecting network access to devices with appropriate mechanisms. To operate the devices in a protected IT environment, Siemens recommends configuring the environment according to Siemens’ Operational Guidelines for Industrial Security and following recommendations in the product manuals.
For additional information, please refer to Siemens Security Advisory SSA-491621
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage at cisa.gov/ics. Several CISA products detailing cyber defense best practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage at cisa.gov/ics in the technical information paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing suspected malicious activity should follow established internal procedures and report findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.