All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 8.3
- ATTENTION: Exploitable remotely, public exploits are available
- Vendor: Omron
- Equipment: NJ/NX-series Machine Automation Controllers
- Vulnerability: Active Debug Code
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an attacker to obtain unauthorized access to the device and cause the device to be in an “out of service” state or execute a malicious program on the device.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following products of the NJ/NX-series Machine Automation Controllers are affected:
- NX7-series Machine Automation Controller (All Models): Versions 1.28 and prior
- NX1-series Machine Automation Controller (All Models): Versions 1.48 and prior
- NJ-series Machine Automation Controller (All Models): Versions 1.48 and prior
3.2 VULNERABILITY OVERVIEW
An attacker who can analyze the communication of the affected product and perform capture-replay can find unintended entry points into the affected product and cause a denial-of-service condition or execute a malicious program.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Japan
Reid Wightman of Dragos reported this vulnerability to CISA.
Omron recommends updating versions of NJ/NX-series machine automation controllers to address this vulnerability. These updates are available to users by contacting their Omron or distributors:
- NX7-series Machine Automation Controller (All Models): Versions 1.29 or higher
- NX1-series Machine Automation Controller (All Models): Versions 1.50 or higher
- NJ-series Machine Automation Controller (NJ501-1300, NJ501-1400, NJ501-1500): Versions 1.49 or higher
- NJ-series Machine Automation Controller (All other Models): Versions 1.50 or higher
Omron recommends users take the following mitigation measures to minimize the risk of exploitation of this vulnerability:
Enable antivirus protection:
- Protect any PC with access to the control system against malware by ensuring the installation and maintenance of up-to-date commercial grade antivirus software protection.
Implement security measures to prevent unauthorized access:
- Minimize connection of control systems and equipment to open networks preventing untrusted devices from accessing them.
- Implement firewalls by shutting down unused communications ports, limiting communications between hosts, and isolate affected systems from the IT network.
- Use a virtual private network (VPN) for remote access to control systems and equipment.
- Use strong passwords and change passwords frequently.
- Install physical controls that only permit authorized personnel access to control systems and equipment.
- Scan USB drives or similar devices for viruses and malware to ensure the devices are safe before connecting them to systems and devices.
- When possible, enforce multifactor authentication (MFA) on all devices with remote access to control systems and equipment.
Protect data input and output:
- Perform process validation, such as backup validation or range checks, to cope with unintentional modification of input/output data to control systems and devices.
Use data recovery:
- Conduct periodical data backups and maintenance to prepare for potential data loss.
For more information see Omron’s advisory: OMSR-2022-002
This vulnerability and countermeasures correspond to the those reported in the CISA ICS Alert: APT Cyber Tools Targeting ICS/SCADA Devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage at cisa.gov/ics. Several CISA products detailing cyber defense best practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage at cisa.gov/ics in the technical information paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing suspected malicious activity should follow established internal procedures and report findings to CISA for tracking and correlation against other incidents.
This vulnerability has a high attack complexity.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.